A trusted name in fire protection for your business.
No. Fire sprinklers are heat activated. Each sprinkler head discharges individually when activated by heat.
Yes! In most jurisdictions, inspections are completed on an annual basis. Some inspections may need to be completed on a quarterly basis. Call us so that we can put together a protection plan that is custom tailored to suit your needs.
YES!! We recommend that the interior temperature where a wet sprinkler system is located to be maintained at a minimum of 55 degrees Fahrenheit. If you have a dry system, the riser room should be maintained at 55 degrees as well. All low point drains should be drained before the temperatures drop to freezing.
The required clearance between a sprinkler head and storage is 18″.
Inspections ensure that your sprinkler system is working properly. You want to avoid finding out about a malfunction during an emergency.
No. 90% of all fires are controlled with 6 or less sprinkler heads.